SOLIS(8)
========

NAME
----

solis - Driver for Brazilian Microsol SOLIS UPS equipment

NOTE
----

This man page only documents the hardware-specific features of the
solis driver.  For information about the core driver, see
linkman:nutupsdrv[8].

SUPPORTED HARDWARE
------------------
This driver has been tested with :
  
 * Solis   1000 VA
 * Solis   1500 VA
 * Solis   2000 VA
 * Solis   3000 VA
 * Back-UPS BZ1200-BR
 * Back-UPS BZ2200BI-BR

All Solis models are sinusoidal on-line.

In 2009, Schneider Electric acquired Microsol Technologies, and by 2012, the
entire Microsol line of equipment was being sold under the APC brand.

EXTRA ARGUMENTS
---------------

This driver support the following extra optional settings in the
linkman:ups.conf[5].

*battext = n* - (default = 0, no extra battery, where n = Ampere*hour )

*prgshut = 1* - (default = 0, no programable shutdown )

COMMANDS
--------

 * shutdown.return - Shut down in .3 minutes and restart in .3 minutes

 * shutdown.stayoff - Shut down in .3 minutes and do not return

ISSUES
------

The APC version of the Microsol protocol is slightly incompatible with the
*solis* driver. As of version 0.62 of the *solis* driver, the driver will
connect to the UPS, but some values are read incorrectly.

AUTHOR
------
Silvino B. Magalhães <sbm2yk@gmail.com>

SEE ALSO
--------

The core driver:
~~~~~~~~~~~~~~~~
linkman:nutupsdrv[8]

Internet resources:
~~~~~~~~~~~~~~~~~~~
The NUT (Network UPS Tools) home page: http://www.networkupstools.org/
