ifndef::external_title[]
NUT command and variable naming scheme
======================================
endif::external_title[]

This is a dump of the standard variables and command names used in NUT.
Don't use a name with any of the dstate functions unless it exists here.

If you need a new variable or command name, contact the Development Team
first.

Put another way: if you make up a name that's not in this list and it
gets into the tree, and then we come up with a better name later, clients
that use the undocumented variable will break when it is changed.

NOTE: "opaque" means programs should not attempt to parse the value for
that variable as it may vary greatly from one UPS to the next. These
strings are best handled directly by the user.

Variables
---------

device: General unit information
~~~~~~~~~~~~~~~~~~~~~~~~~~~~~~~~

NOTE: some of these data will be redundant with ups.* information
during a transition period. The ups.* data will then be removed.

[options="header"]
|====================================================================================
| Name                | Description                                | Example value
| device.model        | Device model                               | BladeUPS
| device.mfr          | Device manufacturer                        | Eaton
| device.serial       | Device serial number (opaque string)       | WS9643050926
| device.type         | Device type (ups, pdu, scd, psu, ats)      | ups
| device.description  | Device description (opaque string)         | Some ups
| device.contact      | Device administrator name (opaque string)  | John Doe
| device.location     | Device physical location (opaque string)   | 1st floor
| device.part         | Device part number (opaque string)         | 123456789
| device.macaddr      | Physical network address of the device     | 68:b5:99:f5:89:27 
| device.uptime       | Device uptime in seconds                   | 1782
|=====================================================================================

ups: General unit information
~~~~~~~~~~~~~~~~~~~~~~~~~~~~~

[options="header"]
|===============================================================================
| Name                  | Description                  | Example value
| ups.status            | UPS status                   | linkdoc:developer-guide[OL,_status_data]
| ups.alarm             | UPS alarms                   | OVERHEAT
| ups.time              | Internal UPS clock time
                          (opaque string)              | 12:34
| ups.date              | Internal UPS clock date
                          (opaque string)              | 01-02-03
| ups.model             | UPS model                    | SMART-UPS 700
| ups.mfr               | UPS manufacturer             | APC
| ups.mfr.date          | UPS manufacturing date
                          (opaque string)              | 10/17/96
| ups.serial            | UPS serial number (opaque    
                          string)                      | WS9643050926
| ups.vendorid          | Vendor ID for USB devices    | 0463
| ups.productid         | Product ID for USB devices   | 0001
| ups.firmware          | UPS firmware (opaque string) | 50.9.D
| ups.firmware.aux      | Auxiliary device firmware    | 4Kx
| ups.temperature       | UPS temperature (degrees C)  | 042.7
| ups.load              | Load on UPS (percent)        | 023.4
| ups.load.high         | Load when UPS
                          switches to overload
                          condition ("OVER") (percent) | 100
| ups.id                | UPS system identifier
                          (opaque string)              | Sierra
| ups.delay.start       | Interval to wait before
                          restarting the load
                          (seconds)                    | 0
| ups.delay.reboot      | Interval to wait before
                          rebooting the UPS (seconds)  | 60
| ups.delay.shutdown    | Interval to wait after
                          shutdown with delay command
                          (seconds)                    | 20
| ups.timer.start       | Time before the load will be
                          started (seconds)            | 30
| ups.timer.reboot      | Time before the load will be
                          rebooted (seconds)           | 10
| ups.timer.shutdown    | Time before the load will be
                          shutdown (seconds)           | 20
| ups.test.interval     | Interval between self tests
                          (seconds)                    | 1209600 (two weeks)
| ups.test.result       | Results of last self test
                          (opaque string)              | Bad battery pack
| ups.test.date         | Date of last self test
                          (opaque string)              | 07/17/12
| ups.display.language  | Language to use on front
                          panel (*** opaque)           | E
| ups.contacts          | UPS external contact sensors
                          (*** opaque)                 | F0
| ups.efficiency        | Efficiency of the UPS (ratio
                          of the output current on the
                          input current) (percent)     | 95
| ups.power             | Current value of apparent
                          power (Volt-Amps)            | 500
| ups.power.nominal     | Nominal value of apparent
                          power (Volt-Amps)            | 500
| ups.realpower         | Current value of real
                          power (Watts)                | 300
| ups.realpower.nominal | Nominal value of real
                          power (Watts)                | 300
| ups.beeper.status     | UPS beeper status
                          (enabled, disabled or muted) | enabled
| ups.type              | UPS type (*** opaque)        | offline
| ups.watchdog.status   | UPS watchdog status
                          (enabled or disabled)        | disabled
| ups.start.auto        | UPS starts when mains is
                          (re)applied                  | yes
| ups.start.battery     | Allow to start UPS from
                          battery                      | yes
| ups.start.reboot      | UPS coldstarts from battery
                          (enabled or disabled)        | yes
| ups.shutdown          | Enable or disable UPS
                          shutdown ability (poweroff)  | enabled
|===============================================================================

NOTE: When present, the value of *ups.start.auto* has an impact on shutdown.*
commands. For the sake of coherence, shutdown commands will set *ups.start.auto*
to the right value before issuing the command. That is, shutdown.stayoff will first
set *ups.start.auto* to *no*, while shutdown.return will set it to *yes*.

input: Incoming line/power information
~~~~~~~~~~~~~~~~~~~~~~~~~~~~~~~~~~~~~~

[options="header"]
|=================================================================================
| Name                        | Description                       | Example value
| input.voltage               | Input voltage (V)                 | 121.5
| input.voltage.maximum       | Maximum incoming voltage seen (V) | 130
| input.voltage.minimum       | Minimum incoming voltage seen (V) | 100
| input.voltage.status        | Status relative to the
                                thresholds                        | critical-low
| input.voltage.low.warning   | Low warning threshold (V)         | 205
| input.voltage.low.critical  | Low critical threshold (V)        | 200
| input.voltage.high.warning  | High warning threshold (V)        | 230
| input.voltage.high.critical | High critical threshold (V)       | 240
| input.voltage.nominal       | Nominal input voltage (V)         | 120
| input.voltage.extended      | Extended input voltage range      | no
| input.transfer.delay        | Delay before transfer to mains
                                (seconds)                         | 60
| input.transfer.reason       | Reason for last transfer
                                to battery (*** opaque)           | T
| input.transfer.low          | Low voltage transfer point (V)    | 91
| input.transfer.high         | High voltage transfer point (V)   | 132
| input.transfer.low.min      | smallest settable low
                                voltage transfer point (V)        | 85
| input.transfer.low.max      | greatest settable low
                                voltage transfer point (V)        | 95
| input.transfer.high.min     | smallest settable high
                                voltage transfer point (V)        | 131
| input.transfer.high.max     | greatest settable high
                                voltage transfer point (V)        | 136
| input.sensitivity           | Input power sensitivity           | H (high)
| input.quality               | Input power quality (***
                                opaque)                           | FF
| input.current               | Input current (A)                 | 4.25
| input.current.nominal       | Nominal input current (A)         | 5.0
| input.current.status        | Status relative to the
                                thresholds                        | critical-high
| input.current.low.warning   | Low warning threshold (A)         | 4
| input.current.low.critical  | Low critical threshold (A)        | 2
| input.current.high.warning  | High warning threshold (A)        | 10
| input.current.high.critical | High critical threshold (A)       | 12
| input.frequency             | Input line frequency (Hz)         | 60.00
| input.frequency.nominal     | Nominal input line
                                frequency (Hz)                    | 60
| input.frequency.status      | Frequency status                  | out-of-range
| input.frequency.low         | Input line frequency low (Hz)     | 47
| input.frequency.high        | Input line frequency high (Hz)    | 63
| input.frequency.extended    | Extended input frequency range    | no
| input.transfer.boost.low    | Low voltage boosting
                                transfer point (V)                | 190
| input.transfer.boost.high   | High voltage boosting
                                transfer point (V)                | 210
| input.transfer.trim.low     | Low voltage trimming
                                transfer point (V)                | 230
| input.transfer.trim.high    | High voltage trimming
                                transfer point (V)                | 240
| input.load                  | Load on (ePDU) input (percent
                                of full)                          | 25
| input.realpower             | Current sum value of all (ePDU)
                                phases real power (W)             | 300
| input.power                 | Current sum value of all (ePDU)
                                phases apparent power (VA)        | 500
| input.source                | The current input power source    | 1
| input.source.preferred      | The preferred power source         | 1
|=================================================================================

output: Outgoing power/inverter information
~~~~~~~~~~~~~~~~~~~~~~~~~~~~~~~~~~~~~~~~~~~

[options="header"]
|===============================================================================
| Name                      | Description                    | Example value
| output.voltage            | Output voltage (V)             | 120.9
| output.voltage.nominal    | Nominal output voltage (V)     | 120
| output.frequency          | Output frequency (Hz)          | 59.9
| output.frequency.nominal  | Nominal output frequency (Hz)  | 60
| output.current            | Output current (A)             | 4.25
| output.current.nominal    | Nominal output current (A)     | 5.0
|===============================================================================

Three-phase additions
~~~~~~~~~~~~~~~~~~~~~

The additions for three-phase measurements would produce a very long table
due to all the combinations that are possible, so these additions are
broken down to their base components.

Phase Count Determination
^^^^^^^^^^^^^^^^^^^^^^^^^
input.phases (3 for three-phase, absent or 1 for 1phase)
output.phases (as for input.phases)

DOMAINs
^^^^^^^
Any input or output is considered a valid DOMAIN.

input (should really be called input.mains, but keep this for compat)
input.bypass
input.servicebypass

output (should really be called output.load, but keep this for compat)
output.bypass
output.inverter
output.servicebypass

Specification (SPEC)
^^^^^^^^^^^^^^^^^^^^

Voltage, current, frequency, etc are considered to be a specification of
the measurement.

With this notation, the old 1phase naming scheme becomes DOMAIN.SPEC
Example: `input.current`

CONTEXT
^^^^^^^

When in three-phase mode, we need some way to specify the target for most
measurements in more detail. We call this the CONTEXT.

With this notation, the naming scheme becomes DOMAIN.CONTEXT.SPEC when
in three-phase mode.
Example: `input.L1.current`

Valid CONTEXTs
^^^^^^^^^^^^^^

 L1-L2  \
 L2-L3   \
 L3-L1    for voltage measurements
 L1-N    /
 L2-N   /
 L3-N  /

 L1  \
 L2  for current and power measurements
 L3  /
 N  - for current measurement

Valid SPECs
^^^^^^^^^^^

Valid with/without context (i.e. per phase or aggregated/averaged)

[options="header"]
|===============================================================================
| Name                  | Description
| alarm                 | Alarms for phases, published in ups.alarm
| current               | Current (A)
| current.maximum       | Maximum seen current (A)
| current.minimum       | Minimum seen current (A)
| current.status        | Status relative to the thresholds
| current.low.warning   | Low warning threshold (A)
| current.low.critical  | Low critical threshold (A)
| current.high.warning  | High warning threshold (A)
| current.high.critical | High critical threshold (A)
| current.peak          | Peak current
| voltage               | Voltage (V)
| voltage.nominal       | Nominal voltage (V)
| voltage.maximum       | Maximum seen voltage (V)
| voltage.minimum       | Minimum seen voltage (V)
| voltage.status        | Status relative to the thresholds 
| voltage.low.warning   | Low warning threshold (V)
| voltage.low.critical  | Low critical threshold (V)
| voltage.high.warning  | High warning threshold (V)
| voltage.high.critical | High critical threshold (V)
| power                 | Apparent power (VA)
| power.maximum         | Maximum seen apparent power (VA)
| power.minimum         | Minimum seen apparent power (VA)
| power.percent         | Percentage of apparent power related to maximum load
| power.maximum.percent | Maximum seen percentage of apparent power
| power.minimum.percent | Minimum seen percentage of apparent power
| realpower             | Real power (W)
| powerfactor           | Power Factor (dimensionless value between 0.00 and 1.00)
| crestfactor           | Crest Factor (dimensionless value greater or equal to 1)
| load                  | Load on (ePDU) input
|===============================================================================

Valid without context (i.e. aggregation of all phases):

[options="header"]
|===============================================================================
| Name                  | Description
| frequency             | Frequency (Hz)
| frequency.nominal     | Nominal frequency (Hz)
| realpower             | Current value of real power (Watts)
| power                 | Current value of apparent power (Volt-Amps)
|===============================================================================

EXAMPLES
~~~~~~~~

Partial Three phase - Three phase example:

	input.phases: 3
	input.frequency: 50.0
	input.L1.current: 133.0
	input.bypass.L1-L2.voltage: 398.3
	output.phases: 3
	output.L1.power: 35700
	output.powerfactor: 0.82

Partial Three phase - One phase example:

	input.phases: 3
	input.L2.current: 48.2
	input.N.current: 3.4
	input.L3-L1.voltage: 405.4
	input.frequency: 50.1
	output.phases: 1
	output.current: 244.2
	output.voltage: 120
	output.frequency.nominal: 60.0

battery: Any battery details
~~~~~~~~~~~~~~~~~~~~~~~~~~~~

[options="header"]
|===============================================================================
| Name                         | Description                         | Example value
| battery.charge               | Battery charge (percent)            | 100.0
| battery.charge.low           | Remaining battery level when
                                 UPS switches to LB (percent)        | 20
| battery.charge.restart       | Minimum battery level for
                                 UPS restart after power-off         | 20
| battery.charge.warning       | Battery level when UPS switches
                                 to "Warning" state (percent)        | 50
| battery.charger.status       | Status of the battery charger
                                 (see the note below)                | charging
| battery.voltage              | Battery voltage (V)                 | 24.84
| battery.voltage.nominal      | Nominal battery voltage (V)         | 024
| battery.voltage.low          | Minimum battery voltage, that
                                 triggers FSD status                 | 21,52
| battery.voltage.high         | Maximum battery voltage
                                 (i.e. battery.charge = 100)         | 26,9
| battery.capacity             | Battery capacity (Ah)               | 7.2
| battery.current              | Battery current (A)                 | 1.19
| battery.current.total        | Total battery current (A)           | 1.19
| battery.temperature          | Battery temperature (degrees C)     | 050.7
| battery.runtime              | Battery runtime (seconds)           | 1080
| battery.runtime.low          | Remaining battery runtime when
                                 UPS switches to LB (seconds)        | 180
| battery.runtime.restart      | Minimum battery runtime for UPS
                                 restart after power-off (seconds)   | 120
| battery.alarm.threshold      | Battery alarm threshold             | 0 (immediate)
| battery.date                 | Battery change date (opaque string) | 11/14/00
| battery.mfr.date             | Battery manufacturing date 
                                 (opaque string)                     | 2005/04/02
| battery.packs                | Number of battery packs             | 001
| battery.packs.bad            | Number of bad battery packs         | 000
| battery.type                 | Battery chemistry (opaque
                                 string)                             | PbAc
| battery.protection           | Prevent deep discharge of
                                 battery                             | yes
| battery.energysave           | Switch off when running on
                                 battery and no/low load             | no
| battery.energysave.load      | Switch off UPS if on battery and
                                 load level lower (percent)          | 5
| battery.energysave.delay     | Delay before switch off UPS if on
                                 battery and load level low (min)    | 3
| battery.energysave.realpower | Switch off UPS if on battery
                                 and load level lower (Watts)        | 10
|===============================================================================

NOTE:
battery.charger.status replaces the historic flags CHRG and DISCHRG that were
exposed through ups.status.  battery.charger.status can have one of the
following value:

- charging: battery is charging,
- discharging: battery is discharging,
- floating: battery has completed its charge cycle, and waiting to go to resting
mode,
- resting: the battery is fully charged, and not charging nor discharging.


ambient: Conditions from external probe equipment
~~~~~~~~~~~~~~~~~~~~~~~~~~~~~~~~~~~~~~~~~~~~~~~~~

NOTE: multiple sensors can be exposed using the indexed notation.
'ambient.*', without index or using '0', relates to the embedded sensor.
For example: 'ambient.temperature' represent the embedded sensor temperature.
Other sensors (external, communication card, ...) can use indexes
from '1' to 'n'. For example: 'ambient.1.temperature' for the first external
sensor temperature.

[options="header"]
|==================================================================================
| Name                                | Description                 | Example value
| ambient.n.present                   | Ambient sensor presence     | yes
| ambient.n.temperature               | Ambient temperature
                                        (degrees C)                 | 25.40
| ambient.n.temperature.alarm         | Temperature alarm
                                        (enabled/disabled)          | enabled
| ambient.n.temperature.status        | Ambient temperature status
                                        relative to the thresholds  | warning-low
| ambient.n.temperature.high          | Temperature threshold high
                                        (degrees C)                 | 60
| ambient.n.temperature.high.warning  | Temperature threshold high
                                        warning (degrees C)         | 40
| ambient.n.temperature.high.critical | Temperature threshold high
                                        critical (degrees C)        | 60
| ambient.n.temperature.low           | Temperature threshold low
                                        (degrees C)                 | 5
| ambient.n.temperature.low.warning   | Temperature threshold low
                                        warning (degrees C)         | 10
| ambient.n.temperature.low.critical  | Temperature threshold low
                                        critical (degrees C)        | 5
| ambient.n.temperature.maximum       | Maximum temperature seen
                                        (degrees C)                 | 37.6
| ambient.n.temperature.minimum       | Minimum temperature seen
                                        (degrees C)                 | 18.1
| ambient.n.humidity                  | Ambient relative humidity
                                        (percent)                   | 038.8
| ambient.n.humidity.alarm            | Relative humidity alarm
                                        (enabled/disabled)          | enabled
| ambient.n.humidity.status           | Ambient humidity status
                                        relative to the thresholds  | warning-low
| ambient.n.humidity.high             | Relative humidity
                                        threshold high (percent)    | 80
| ambient.n.humidity.high.warning     | Relative humidity threshold
                                        high warning (percent)      | 70
| ambient.n.humidity.high.critical    | Relative humidity threshold
                                        high critical (percent)     | 80
| ambient.n.humidity.low              | Relative humidity
                                        threshold low (percent)     | 10
| ambient.n.humidity.low.warning      | Relative humidity threshold
                                        low warning (percent)       | 20
| ambient.n.humidity.low.critical     | Relative humidity threshold
                                        low critical (percent)      | 10
| ambient.n.humidity.maximum          | Maximum relative humidity
                                        seen (percent)              | 60
| ambient.n.humidity.minimum          | Minimum relative humidity
                                        seen (percent)              | 13
| ambient.n.contacts.x.status         | State of the dry contact
                                        sensor x                    | open
|==================================================================================


outlet: Smart outlet management
~~~~~~~~~~~~~~~~~~~~~~~~~~~~~~~

NOTE: *n* stands for the outlet index. For more information, refer to the
NUT outlets management and PDU notes chapter of the user manual.
A special case is "outlet.0" which is equivalent to "outlet" (without
index), and represent the whole set of outlets of the device. The most
important data is "outlet.count", used to iterate over the whole set of
outlets.

[options="header"]
|===============================================================================
| Name                           | Description                 | Example value
| outlet.count                   | Total number of outlets     | 12
| outlet.n.id                    | Outlet system identifier
                                   (opaque string)             | 1
| outlet.n.desc                  | Outlet name / description
                                   (opaque string)             | Main outlet
| outlet.n.groupid               | Identifier of the group to
                                   which the outlet belongs to | 1
| outlet.n.switch                | Outlet switch control
                                   (on/off)                    | on
| outlet.n.status                | Outlet switch status
                                   (on/off)                    | on
| outlet.n.alarm                 | Alarms for outlets and PDU,
                                   published in ups.alarm      | outlet 1 low
                                                                 voltage warning
| outlet.n.switchable            | Outlet switch ability
                                   (yes/no)                    | yes
| outlet.n.autoswitch.charge.low | Remaining battery level to
                                   power off this outlet
                                   (percent)                   | 80
| outlet.n.battery.charge.low    | Remaining battery level to
                                   power off this outlet
                                   (percent)                   | 80
| outlet.n.delay.shutdown        | Interval to wait before
                                   shutting down this outlet
                                   (seconds)                   | 180
| outlet.n.delay.start           | Interval to wait before
                                   restarting this outlet
                                   (seconds)                   | 120
| outlet.n.timer.shutdown        | Time before the outlet load
                                   will be shutdown (seconds)  | 20
| outlet.n.timer.start           | Time before the outlet load
                                   will be started (seconds)   | 30
| outlet.n.current               | Current (A)                 | 0.19
| outlet.n.current.maximum       | Maximum seen current (A)    | 0.56
| outlet.n.current.status        | Current status relative to
                                   the thresholds              | good
| outlet.n.current.low.warning   | Low warning threshold (A)   | 0.10
| outlet.n.current.low.critical  | Low critical threshold (A)  | 0.05
| outlet.n.current.high.warning  | High warning threshold (A)  | 0.30
| outlet.n.current.high.critical | High critical threshold (A) | 0.40
| outlet.n.realpower             | Current value of real
                                   power (W)                   | 28
| outlet.n.voltage               | Voltage (V)                 | 247.0
| outlet.n.voltage.status        | Voltage status relative to
                                   the thresholds              | good
| outlet.n.voltage.low.warning   | Low warning threshold (V)   | 205
| outlet.n.voltage.low.critical  | Low critical threshold (V)  | 200
| outlet.n.voltage.high.warning  | High warning threshold (V)  | 230
| outlet.n.voltage.high.critical | High critical threshold (V) | 240
| outlet.n.powerfactor           | Power Factor (dimensionless,
                                   value between 0 and 1)      | 0.85
| outlet.n.crestfactor           | Crest Factor (dimensionless,
                                   equal to or greater than 1) | 1.41
| outlet.n.power                 | Apparent power (VA)         | 46
|===============================================================================

outlet.group: groups of smart outlets
^^^^^^^^^^^^^^^^^^^^^^^^^^^^^^^^^^^^^

This is a refinement of the outlet collection, providing grouped
management for a set of outlets. The same principles and data than the
outlet collection apply to outlet.group, especially for the indexing 'n'
and "outlet.group.count". 

Most of the data published for outlets also apply to outlet.group,
including: id, name (similar as outlet "desc"), status, current and
voltage (including status, alarm and thresholds).

Some specific data to outlet groups exists:

[options="header"]
|=================================================================================
| Name                           | Description                    | Example value
| outlet.group.n.type            | Type of outlet group (OPAQUE)  | outlet-section
| outlet.group.n.count           | Number of outlets in the group | 12
|=================================================================================

Example:

	outlet.group.1.current: 0.00
	outlet.group.1.current.high.critical: 16.00
	outlet.group.1.current.high.warning: 12.80
	outlet.group.1.current.low.warning: 0.00
	outlet.group.1.current.nominal: 16.00
	outlet.group.1.current.status: good
	outlet.group.1.id: 1
	outlet.group.1.name: Branch Circuit A
	outlet.group.1.status: on
	outlet.group.1.voltage: 244.23
	outlet.group.1.voltage.high.critical: 265.00
	outlet.group.1.voltage.high.warning: 255.00
	outlet.group.1.voltage.low.critical: 180.00
	outlet.group.1.voltage.low.warning: 190.00
	outlet.group.1.voltage.status: good
	...
	outlet.group.count: 3.00


driver: Internal driver information
~~~~~~~~~~~~~~~~~~~~~~~~~~~~~~~~~~~

[options="header"]
|===============================================================================
| Name                    | Description                  | Example value
| driver.name             | Driver name                  | usbhid-ups
| driver.version          | Driver version (NUT release) | X.Y.Z
| driver.version.internal | Internal driver version      | 1.23.45
| driver.version.data     | Version of the internal data
                            mapping, for generic drivers | Eaton HID 1.31
| driver.parameter.xxx    | Parameter xxx (ups.conf or
                            cmdline -x) setting          | (varies)
| driver.flag.xxx         | Flag xxx (ups.conf or
                            cmdline -x) status           | enabled (or absent)
|===============================================================================

server: Internal server information
~~~~~~~~~~~~~~~~~~~~~~~~~~~~~~~~~~~

[options="header"]
|===============================================================================
| Name           | Description        | Example value
| server.info    | Server information | Network UPS Tools upsd vX.Y.Z -
                                        http://www.networkupstools.org/
| server.version | Server version     | X.Y.Z
|===============================================================================

Instant commands
----------------

[options="header"]
|========================================================================
| Name                     | Description
| load.off                 | Turn off the load immediately
| load.on                  | Turn on the load immediately
| load.off.delay           | Turn off the load possibly after a delay 
| load.on.delay            | Turn on the load possibly after a delay 
| shutdown.return          | Turn off the load possibly after a delay 
                             and return when power is back
| shutdown.stayoff         | Turn off the load possibly after a delay
                             and remain off even if power returns
| shutdown.stop            | Stop a shutdown in progress
| shutdown.reboot          | Shut down the load briefly while rebooting the UPS
| shutdown.reboot.graceful | After a delay, shut down the load briefly
                             while rebooting the UPS
| test.panel.start         | Start testing the UPS panel
| test.panel.stop          | Stop a UPS panel test
| test.failure.start       | Start a simulated power failure
| test.failure.stop        | Stop simulating a power failure
| test.battery.start       | Start a battery test
| test.battery.start.quick | Start a "quick" battery test
| test.battery.start.deep  | Start a "deep" battery test
| test.battery.stop        | Stop the battery test
| test.system.start        | Start a system test
| calibrate.start          | Start runtime calibration
| calibrate.stop           | Stop runtime calibration
| bypass.start             | Put the UPS in bypass mode
| bypass.stop              | Take the UPS out of bypass mode
| reset.input.minmax       | Reset minimum and maximum input voltage status
| reset.watchdog           | Reset watchdog timer (forced reboot of load)
| beeper.enable            | Enable UPS beeper/buzzer
| beeper.disable           | Disable UPS beeper/buzzer
| beeper.mute              | Temporarily mute UPS beeper/buzzer
| beeper.toggle            | Toggle UPS beeper/buzzer
| outlet.n.shutdown.return | Turn off the outlet possibly after a delay 
                             and return when power is back
| outlet.n.load.off        | Turn off the outlet immediately
| outlet.n.load.on         | Turn on the outlet immediately
| outlet.n.load.cycle      | Power cycle the outlet immediately
| outlet.n.shutdown.return | Turn off the outlet and return when power is back
|========================================================================
