Configuration notes
===================

This chapter describe most of the configuration and use aspects of NUT,
including establishing communication with the device and configuring safe
shutdowns when the UPS battery runs out of power.

There are many programs and <<Features,features>> in this
package.  You should check out the <<Overview,NUT Overview>>
and other accompanying documentation to see how it all works.

NOTE: NUT does not currently provide proper graphical configuration tools.
However, there is now support for linkdoc:developer-guide[Augeas,augeas_user],
which will enable the easier creation of configuration tools.
Moreover, linkman:nut-scanner[8] is available to discover supported devices
(USB, SNMP, Eaton XML/HTTP and IPMI) and NUT servers (using Avahi or the classic
connection method).

Details about the configuration files
-------------------------------------

Generalities
~~~~~~~~~~~~

All configuration files within this package are parsed with a common
state machine, which means they all can use a number of extras described here.

First, most of the programs use an uppercase word to declare a
configuration directive.  This may be something like MONITOR, NOTIFYCMD,
or ACCESS.  The case does matter here.  "monitor" won't be recognized.

Next, the parser does not care about whitespace between words.  If you
like to indent things with tabs or spaces, feel free to do it here.

If you need to set a value to something containing spaces, it has to be
contained within "quotes" to keep the parser from splitting up the line.
That is, you want to use something like this:

	SHUTDOWNCMD "/sbin/shutdown -h +0"

Without the quotes, it would only see the first word on the line.

OK, so let's say you really need to embed that kind of quote within your
configuration directive for some reason.  You can do that too.

	NOTIFYCMD "/bin/notifyme -foo -bar \"hi there\" -baz"

In other words, `\` can be used to escape the `"`.

Finally, for the situation where you need to put the `\` character into your
string, you just escape it.

	NOTIFYCMD "/bin/notifyme c:\\dos\\style\\path"

The `\` can actually be used to escape any character, but you only really
need it for `\`, `"`, and `#` as they have special meanings to the parser.

When using file names with space characters, you may end up having tricky
things since you need to write them inside `""` which must be escaped:

	NOTIFYCMD "\"c:\\path with space\\notifyme\" \"c:\\path with space\\name\""

`#` is the comment character.  Anything after an unescaped `#` is ignored.

Something like this...

	identity = my#1ups

will actually turn into `identity = my`, since the `#` stops the
parsing. If you really need to have a `#` in your configuration, then
escape it.

	identity = my\#1ups

Much better.

The `=` character should be used with care too. There should be only one
"simple" `=` character in a line: between the parameter name and its value.
All other `=` characters should be either escaped or within "quotes".

	password = 123=123

is incorrect. You should use:

	password = 123\=123

or:

	password = "123=123"

Line spanning
~~~~~~~~~~~~~

You can put a backslash at the end of the line to join it to the next
one.  This creates one virtual line that is composed of more than one
physical line.

Also, if you leave the `""` quote container open before a newline, it will
keep scanning until it reaches another one.  If you see bizarre behavior
in your configuration files, check for an unintentional instance of
quotes spanning multiple lines.


Basic configuration
-------------------

This chapter describe the base configuration to establish communication with
the device.

This will be sufficient for PDU. But for UPS and SCD, you will also need to
configure <<UPS_shutdown,automatic shutdowns for low battery events>>.

image:images/simple.png[]

[[Driver_configuration]]
Driver configuration
~~~~~~~~~~~~~~~~~~~~

Create one section per UPS in /usr/local/ups/etc/ups.conf

To find out which driver to use, check the <<HCL,Hardware Compatibility List>>,
or data/driver.list.

Once you have picked a driver, create a section for your UPS in
ups.conf.  You must supply values for "driver" and "port".

Some drivers may require other flags or settings.  The "desc" value
is optional, but is recommended to provide a better description of
what your UPS is supporting.

A typical device without any extra settings looks like this:

	[mydevice]
		driver = mydriver
		port = /dev/ttyS1
		desc = "Workstation"

NOTE: USB drivers (usbhid-ups, bcmxcp_usb, tripplite_usb, blazer_usb and
richcomm_usb) are special cases and ignore the 'port' value.
You must still set this value, but it does not matter what you set
it to; a common and good practice is to set 'port' to *auto*, but you can
put whatever you like. If you only own one UBS UPS, the driver will
find it automatically. If you own more than one, refer to the driver's
manual page for more information on matching a specific device.

References: linkman:ups.conf[5],
linkman:nutupsdrv[8],
linkman:bcmxcp_usb[8],
linkman:blazer[8],
linkman:richcomm_usb[8],
linkman:tripplite_usb[8],
linkman:usbhid-ups[8]


[[Starting_drivers]]
Starting the driver(s)
~~~~~~~~~~~~~~~~~~~~~~

Start the driver(s) for your hardware:

	/usr/local/ups/sbin/upsdrvctl start

Make sure the driver doesn't report any errors.  It should show a
few details about the hardware and then enter the background.  You
should get back to the command prompt a few seconds later.  For
reference, a successful start of the `usbhid-ups` driver looks like this:

	# /usr/local/ups/sbin/upsdrvctl start
	Network UPS Tools - Generic HID driver 0.34 (2.4.1)
	USB communication driver 0.31
	Using subdriver: MGE HID 1.12
	Detected EATON - Ellipse MAX 1100 [ADKK22008]

If the driver doesn't start cleanly, make sure you have picked the
right one for your hardware.  You might need to try other drivers
by changing the "driver=" value in ups.conf.

Be sure to check the driver's man page to see if it needs any extra
settings in `ups.conf` to detect your hardware.

If it says `can't bind /var/state/ups/...` or similar, then your
state path probably isn't writable by the driver.  Check the
<<StatePath,permissions and mode on that directory>>.

After making changes, try the <<Ownership, Ownership and permissions>> step again.

References: man pages: linkman:nutupsdrv[8], linkman:upsdrvctl[8]


Data server configuration (upsd)
~~~~~~~~~~~~~~~~~~~~~~~~~~~~~~~~

Configure upsd, which serves data from the drivers to the clients.

First, edit upsd.conf to allow access to your client systems. By
default, upsd will only listen to localhost port 3493/tcp. If you want
to connect to it from other machines, you must specify each interface you
want upsd to listen on for connections, optionally with a port number.

	LISTEN 127.0.0.1 3493
	LISTEN ::1 3493

NOTE: Refer to the NUT user manual <<NUT_Security,security chapter>> for
information on how to access and secure upsd clients connections.

Next, create upsd.users.  For now, this can be an empty file.
You can come back and add more to it later when it's time to
configure upsmon or run one of the management tools.

Do not make either file world-readable, since they both hold
access control data and passwords.  They just need to be readable by
the user you created in the preparation process.

The suggested configuration is to chown it to root, chgrp it to the
group you created, then make it readable by the group.

	chown root:nut upsd.conf upsd.users
	chmod 0640 upsd.conf upsd.users

References: man pages: linkman:upsd.conf[5],
linkman:upsd.users[5],
linkman:upsd[8]

[[Starting_upsd]]
Starting the data server
~~~~~~~~~~~~~~~~~~~~~~~~

Start the network data server:

	/usr/local/ups/sbin/upsd

Make sure it is able to connect to the driver(s) on your system.
A successful run looks like this:

	# /usr/local/ups/sbin/upsd
	Network UPS Tools upsd 2.4.1
	listening on 127.0.0.1 port 3493
	listening on ::1 port 3493
	Connected to UPS [eaton]: usbhid-ups-eaton

upsd prints dots while it waits for the driver to respond.  Your
system may print more or less depending on how many drivers you
have and how fast they are.

NOTE: if upsd says that it can't connect to a UPS or that the data
is stale, then your ups.conf is not configured correctly, or you
have a driver that isn't working properly.  You must fix this before
going on to the next step.

Reference: man page: linkman:upsd[8]

Check the UPS data
~~~~~~~~~~~~~~~~~~

Status data
^^^^^^^^^^^

Make sure that the UPS is providing good status data.

	/usr/local/ups/bin/upsc myupsname@localhost ups.status

You should see just one line in response:

	OL

OL means your system is running on line power.  If it says something
else (like OB - on battery, or LB - low battery), your driver was
probably misconfigured during the <<Driver_configuration, Driver configuration>>
step.  If you reconfigure the driver, use `upsdrvctl stop` to stop it, then
start it again as shown in the <<Starting_drivers, Starting driver(s)>> step.

Reference: man page: linkman:upsc[8]


All data
^^^^^^^^

Look at all of the status data which is being monitored.

	/usr/local/ups/bin/upsc myupsname@localhost

What happens now depends on the kind of device and driver you have.
In the list, you should see ups.status with the same value you got
above.  A sample run on a UPS (Eaton Ellipse MAX 1100) looks like this:

	battery.charge: 100
	battery.charge.low: 20
	battery.runtime: 2525
	battery.type: PbAc
	device.mfr: EATON
	device.model: Ellipse MAX 1100
	device.serial: ADKK22008
	device.type: ups
	driver.name: usbhid-ups
	driver.parameter.pollfreq: 30
	driver.parameter.pollinterval: 2
	driver.parameter.port: auto
	driver.version: 2.4.1-1988:1990M
	driver.version.data: MGE HID 1.12
	driver.version.internal: 0.34
	input.sensitivity: normal
	input.transfer.boost.low: 185
	input.transfer.high: 285
	input.transfer.low: 165
	input.transfer.trim.high: 265
	input.voltage.extended: no
	outlet.1.desc: PowerShare Outlet 1
	outlet.1.id: 2
	outlet.1.status: on
	outlet.1.switchable: no
	outlet.desc: Main Outlet
	outlet.id: 1
	outlet.switchable: no
	output.frequency.nominal: 50
	output.voltage: 230.0
	output.voltage.nominal: 230
	ups.beeper.status: enabled
	ups.delay.shutdown: 20
	ups.delay.start: 30
	ups.firmware: 5102AH
	ups.load: 0
	ups.mfr: EATON
	ups.model: Ellipse MAX 1100
	ups.power.nominal: 1100
	ups.productid: ffff
	ups.serial: ADKK22008
	ups.status: OL CHRG
	ups.timer.shutdown: -1
	ups.timer.start: -1
	ups.vendorid: 0463

Reference: man page: linkman:upsc[8],
<<nut-names,NUT command and variable naming scheme>>

Startup scripts
~~~~~~~~~~~~~~~

NOTE: This step is not necessary if you installed from packages.

Edit your startup scripts, and make sure upsdrvctl and upsd are run every time
your system starts.

[[UPS_shutdown]]
Configuring automatic shutdowns for low battery events
------------------------------------------------------

The whole point of UPS software is to bring down the OS cleanly when you
run out of battery power. Everything else is roughly eye candy.

To make sure your system shuts down properly, you will need to perform some
additional configuration and run upsmon. Here are the basics.

[[Shutdown_design]]
Shutdown design
~~~~~~~~~~~~~~~

When your UPS batteries get low, the operating system needs to be brought
down cleanly.  Also, the UPS load should be turned off so that all devices
that are attached to it are forcibly rebooted.

Here are the steps that occur when a critical power event happens:

1. The UPS goes on battery

2. The UPS reaches low battery (a "critical" UPS), that is to say
   upsc displays:
+
   ups.status: OB LB
+
The exact behavior depends on the specific device, and is related to:

   - battery.charge and battery.charge.low
   - battery.runtime and battery.runtime.low

3. The upsmon master notices and sets "FSD" - the "forced shutdown"
   flag to tell all slave systems that it will soon power down the load.
+
(If you have no slaves, skip to step 6)

4. upsmon slave systems see "FSD" and:

   - generate a NOTIFY_SHUTDOWN event
   - wait FINALDELAY seconds - typically 5
   - call their SHUTDOWNCMD
   - disconnect from upsd

5. The upsmon master system waits up to HOSTSYNC seconds (typically 15)
   for the slaves to disconnect from upsd.  If any are connected after
   this time, upsmon stops waiting and proceeds with the shutdown
   process.

6. The upsmon master:

   - generates a NOTIFY_SHUTDOWN event
   - waits FINALDELAY seconds - typically 5
   - creates the POWERDOWNFLAG file - usually /etc/killpower
   - calls the SHUTDOWNCMD

7. On most systems, init takes over, kills your processes, syncs and
   unmounts some filesystems, and remounts some read-only.

8. init then runs your shutdown script.  This checks for the
   POWERDOWNFLAG, finds it, and tells the UPS driver(s) to power off
   the load.

9. The system loses power.

10. Time passes.  The power returns, and the UPS switches back on.

11. All systems reboot and go back to work.


How you set it up
~~~~~~~~~~~~~~~~~

[[NUT_user_creation]]
NUT user creation
^^^^^^^^^^^^^^^^^

Create a upsd user for upsmon to use while monitoring this UPS.

Edit upsd.users and create a new section.  upsmon will connect
to upsd and use this user name (in brackets) and password to
authenticate.  This example is for a user called "monuser":

	[monuser]
		password = mypass
		upsmon master
		# or upsmon slave

References: linkman:upsd[8], linkman:upsd.users[5]

Reloading the data server
^^^^^^^^^^^^^^^^^^^^^^^^^

Reload upsd.  Depending on your configuration, you may be able to
do this without stopping upsd:

	/usr/local/ups/sbin/upsd -c reload

If that doesn't work (check the syslog), just restart it:

	/usr/local/ups/sbin/upsd -c stop
	/usr/local/ups/sbin/upsd

NOTE: if you want to make reloading work later, see the entry in the
link:FAQ.html[FAQ] about starting upsd as a different user.

Power Off flag file
^^^^^^^^^^^^^^^^^^^

Set the POWERDOWNFLAG location for upsmon.

In upsmon.conf, add a POWERDOWNFLAG directive with a filename.
upsmon will create this file when the UPS needs to be powered off
during a power failure when low battery is reached.

We will test for the presence of this file in a later step.

	POWERDOWNFLAG /etc/killpower

References: man pages: linkman:upsmon[8],
linkman:upsmon.conf[5]

Securing upsmon.conf
^^^^^^^^^^^^^^^^^^^^

The recommended setting is to have it owned by root:nut, then make it readable
by the group and not world.  This file contains passwords that could be used by
an attacker to start a shutdown, so keep it secure.

	chown root:nut upsmon.conf
	chmod 0640 upsmon.conf

This step has been placed early in the process so you secure this file before
adding sensitive data in the next step.


Create a MONITOR directive for upsmon
^^^^^^^^^^^^^^^^^^^^^^^^^^^^^^^^^^^^^

Edit upsmon.conf and create a MONITOR line with the UPS definition
(<upsname>@<hostname>), username and password from the <<NUT_user_creation, NUT user creation>>
step, and the master or slave setting.

If it's the master (i.e., it's connected to this UPS directly):

	MONITOR myupsname@mybox 1 monuser mypass master

If it's just monitoring this UPS over the network, and some other system is the
master:

	MONITOR myupsname@mybox 1 monuser mypass slave

The number "1" here is the power value.  This should always be set to 1 unless
you have a very special (read: expensive) system with redundant power supplies.
In such cases, refer to the User Manual:

- <<BigServers,typical setups for big servers>>,
- <<DataRoom,typical setups for data rooms>>.

References: linkman:upsmon[8], linkman:upsmon.conf[5]

Define a SHUTDOWNCMD for upsmon
^^^^^^^^^^^^^^^^^^^^^^^^^^^^^^^

Still in upsmon.conf, add a directive that tells upsmon how to shut down your
system.  This example seems to work on most systems:

	SHUTDOWNCMD "/sbin/shutdown -h +0"

Notice the presence of "quotes" here to keep it together.

If your system has special needs, you may want to set this to a script which
does local shutdown tasks before calling init.


Start upsmon
^^^^^^^^^^^^

	/usr/local/ups/sbin/upsmon

If it complains about something, then check your configuration.

Checking upsmon
^^^^^^^^^^^^^^^

Look for messages in the syslog to indicate success.  It should look something
like this:

	May 29 01:11:27 mybox upsmon[102]: Startup successful
	May 29 01:11:28 mybox upsd[100]: Client monuser@192.168.50.1
	logged into UPS [myupsname]

Any errors seen here are probably due to an error in the config files of either
`upsmon` or `upsd`.  You should fix them before continuing.


Startup scripts
^^^^^^^^^^^^^^^

NOTE: This step is not need if you installed from packages.

Edit your startup scripts, and add a call to `upsmon`.

Make sure `upsmon` starts when your system comes up.  Do it after `upsdrvctl`
and `upsd`, or it will complain about not being able to contact the server.

You may delete the POWERDOWNFLAG in the startup scripts, but it is not
necessary. `upsmon` will clear that file for you when it starts.

NOTE: Init script examples are provide in the 'scripts' directory of
the NUT source tree, and in the various <<_binary_packages,packages>>
that exist.

Shutdown scripts
^^^^^^^^^^^^^^^^

NOTE: This step is not need if you installed from packages.

Edit your shutdown scripts, and add `upsdrvctl shutdown`.

You should configure your system to power down the UPS after the filesystems are
remounted read-only.  Have it look for the presence of the POWERDOWNFLAG (from
linkman:upsmon.conf[5]), using this as an example:

--------------------------------------------------------------------------------

	if (test -f /etc/killpower)
	then
		echo "Killing the power, bye!"
		/usr/local/ups/bin/upsdrvctl shutdown

		sleep 120

		# uh oh... the UPS power-off failed
		# you probably want to reboot here so you don't get stuck!
		# *** see also the section on power races in the FAQ! ***
	fi

--------------------------------------------------------------------------------

[WARNING]
================================================================================
- Be careful that upsdrvctl command will probably power off your machine.
Don't use it unless your system is ready to be halted by force.
If you run RAID, read the <<_raid_warning,RAID warning>> below!

- Make sure the filesystem(s) containing upsdrvctl, ups.conf and your UPS
driver(s) are mounted (possibly in read-only mode) when the system gets to this
point.  Otherwise it won't be able to figure out what to do.
================================================================================


[[Testing_shutdowns]]
Testing shutdowns
^^^^^^^^^^^^^^^^^

UPS equipment varies from manufacturer to manufacturer and even within
model lines.  You should test the <<Shutdown_design,shutdown sequence>>
on your systems before leaving them unattended.  A successful sequence
is one where the OS halts before the battery runs out, and the system
restarts when power returns.

The first step is to see how upsdrvctl will behave without actually turning off
power. To do so, use the '-t' argument:

	/usr/local/ups/bin/upsdrvctl -t shutdown

It will display the sequence without actually calling the drivers.


You can finally test a forced shutdown sequence (FSD) using:

	/usr/local/ups/sbin/upsmon -c fsd

This will execute a full shutdown sequence, as presented in
<<Shutdown_design,Shutdown design>>, starting from the 3rd step.

If everything works correctly, the computer will be forcibly powered
off, may remain off for a few seconds to a few minutes (depending on
the driver and UPS type), then will power on again.

If your UPS just sits there and never resets the load, you are vulnerable
to a power race and should add the "reboot after timeout" hack at the very
least.

Also refer to the section on power races in the link:FAQ.html[FAQ].

Using suspend to disk
~~~~~~~~~~~~~~~~~~~~~

Support for suspend to RAM and suspend to disk has been available in
the Linux kernel for a while now. For obvious reasons, suspending to
RAM isn't particularly useful when the UPS battery is getting low,
but suspend to disk may be an interesting concept.

This approach minimizes the amount of disruption which would be caused
by an extended outage.  The UPS goes on battery, then reaches low
battery, and the system takes a snapshot of itself and halts.  Then it
is turned off and waits for the power to return.

Once the power is back, the system reboots, pulls the snapshot back in,
and keeps going from there.  If the user happened to be away when it
happened, they may return and have no idea that their system actually
shut down completely in the middle.

In order for this to work, you need to shutdown NUT (UPS driver, upsd
server and upsmon client) in the suspend script and start them again in
the resume script.  Don't try to keep them running.  The upsd server
will latch the FSD state (so it won't be usable after resuming) and so
will the upsmon client.  Some drivers may work after resuming, but many
don't and some UPSs will require re-initialization, so it's best not
to keep this running either.

After stopping driver, server and client you'll have to send the UPS
the command to shutdown only if the POWERDOWNFLAG is present.  Note
that most likely you'll have to allow for a grace period after sending
'upsdrvctl shutdown' since the system will still have to take a
snapshot of itself after that.  Not all drivers support this, so before
going down this road, make sure that the one you're using does.

RAID warning
~~~~~~~~~~~~

If you run any sort of RAID equipment, make sure your arrays are either halted
(if possible) or switched to "read-only" mode. Otherwise you may suffer a long
resync once the system comes back up.

The kernel may not ever run its final shutdown procedure, so you must take care
of all array shutdowns in userspace before upsdrvctl runs.

If you use software RAID (md) on Linux, get mdadm and try using
'mdadm --readonly' to put your arrays in a safe state. This has to
happen after your shutdown scripts have remounted the filesystems.

On hardware RAID or other kernels, you have to do some detective work. It may
be necessary to contact the vendor or the author of your driver to find out
how to put the array in a state where a power loss won't leave it "dirty".

Our understanding is that most if not all RAID devices on Linux will be fine
unless there are pending writes.  Make sure your filesystems are remounted
read-only and you should be covered.


[[DataRoom]]
Typical setups for enterprise networks and data rooms
-----------------------------------------------------

The split nature of this UPS monitoring software allows a wide variety of
power connections.  This chapter will help you identify how things should
be configured using some general descriptions.

There are two main elements:

1. There's a UPS attached to a communication (serial, USB or network) port on
this system.
2. This system depends on a UPS for power.

You can play "mix and match" with those two to arrive at these descriptions
for individual hosts:

- A: 1 but not 2
- B: 2 but not 1
- C: 1 and 2

A small to medium sized data room usually has one C and a bunch of Bs.
This means that there's a system (type C) hooked to the UPS which depends
on it for power.  There are also some other systems in there (type B)
which depend on that same UPS for power, but aren't directly connected to
it.

Larger data rooms or those with multiple UPSes may have several "clusters"
of the "single C, many Bs" depending on how it's all wired.

Finally, there's a special case.  Type A systems are connected to a UPS's
serial port, but don't depend on it for power.  This usually happens when
a UPS is physically close to a box and can reach the serial port, but
the wiring is such that it doesn't actually feed it.

Once you identify a system's type, use this list to decide which of the
programs need to be run for monitoring:

- A: driver and upsd
- B: upsmon (as slave)
- C: driver, upsd, and upsmon (as master)

To further complicate things, you can have a system that is hooked to
multiple UPSes, but only depends on one for power.  This particular
situation makes it an "A" relative to one UPS, and a "C" relative to the
other.  The software can handle this - you just have to tell it what to do.

NOTE: NUT can also serve as a data proxy to increase the number of clients,
or share the communication load between several upsd instances.

image:images/advanced.png[]

If you are running large server-class systems that have more than one
power feed, see the next section for information on how to handle it
properly.

[[BigServers]]
Typical setups for big servers with UPS redundancy
--------------------------------------------------

By using multiple MONITOR statements in upsmon.conf, you can configure an
environment where a large machine with redundant power monitors multiple
separate UPSes.

image:images/bigbox.png[]

Example configuration
~~~~~~~~~~~~~~~~~~~~~

For the examples in this section, we will use a server with four power supplies
installed.

Two UPS, 'Alpha' and 'Beta', are each driving two of the power supplies.
This means that either 'Alpha' *or* 'Beta' can totally shut down and the
server will be able to keep running.

The upsmon.conf configuration that reflect this is the following:

	MONITOR ups-alpha@myhost 2 monuser mypass master
	MONITOR ups-beta@myhost 2 monuser mypass master
	MINSUPPLIES 2

With that configuration, upsmon will only shut down when both UPS reaches
a critical (on battery + low battery) condition, since 'Alpha' and 'Beta'
provide the same power value.

As an added bonus, this means you can move a running server from one UPS
to another (for maintenance purpose for example) without bringing it down since
the minimum power will be provided at all times.

The MINSUPPLIES line tells upsmon that we need at least 2 power supplies
to be receiving power from a good UPS (on line or on battery, just not
on battery and low battery).

NOTE: we could have used a 'Power Value' of 1 for both UPS, and MINSUPPLIES
set to 1 too. These values are purely arbitrary, so you are free to use your
own rules. Here, we have linked these values to the number of power supplies
that each UPS is feeding (2).


Multiple UPS shutdowns ordering
~~~~~~~~~~~~~~~~~~~~~~~~~~~~~~~

If you have multiple UPSes connected to your system, chances are that you
need to shut them down in a specific order.  The goal is to shut down
everything but the one keeping upsmon alive at first, then you do that one
last.

To set the order in which your UPSes receive the shutdown commands, define
the 'sdorder' value in your ups.conf.

	[bigone]
		driver = usbhid-ups
		port = auto
		sdorder = 2

	[littleguy]
		driver = mge-shut
		port = /dev/ttyS0
		sdorder = 1

	[misc]
		driver = blazer_ser
		port = /dev/ttyS1
		sdorder = 0

The order runs from 0 to the highest number available.  So, for this
configuration, the order of shutdowns would be 'misc', 'littleguy', and then
'bigone'.

NOTE: If you have a UPS that shouldn't be shutdown when running 'upsdrvctl
shutdown', set the *sdorder* to *-1*.


Other redundancy configurations
~~~~~~~~~~~~~~~~~~~~~~~~~~~~~~~

There are a lot of ways to handle redundancy and they all come down to how many
power supplies, power cords and independent UPS connections you have.  A
system with a 1:1 cord:supply ratio has more wires stuffed behind it, but
it's much easier to move things around since any given UPS drives a smaller
percentage of the overall power.

More information can be found in the linkdoc:user-manual[NUT user manual],
and the various link:man/index.html[user manual pages].
